Response to This heater does have a water pressure switch and has a thermostat, so it does sense both water flow and temperature. Since your house is at 5,600 you would need a Raypak High Elevation Heater. The 206,000 BTU Raypak heater has a minimum flow rating of 20 Gallons Per Minute (GPM) and a max flow rating of 120 GPM's. Based on these flow ratings any pump from 1/2 HP to 2 HP would work fine with this heater.
An image is worth 1,000 words! Add an image or two to your comment to help ensure it is understood accurately.
Yes, please email me exclusive discounts, swimming pool tips and helpful how to guides.
This comment may be posted on a public site. Do not include: HTML, references to other retailers, pricing, personal information, or any profane, inflammatory language.